Cost-effective solar inverter This is a multi-functional inverter/charger, combining functions of inverter, solar charger and battery charger to offer uninterruptible power support in portable size. Its comprehensive LCD display offers user-configurable and easy-accessible button operation such as battery charging current, AC/solar charger priority, and acceptable input voltage based on different applications.
- Requires 12V DC battery input. You can parallel up to 3 x 12V batteries to maintain the voltage.
- There is a 500W MPPT Solar input to trickle charge the battery. This is inverter is more for backup purposes.
- This is a pure sine wave inverter
Recommended application: Lights and LED TV, Decoder, alarm and fridge (must be under 1000W)
The box excludes any electrical power cables. An electrician is required to install this unit.
All inverters must be installed by a qualified electrical wireman or Master electrician with a valid registration with the Department of Labour. A valid electrical certificate of compliance (Coc) must be issued once installed, specific to the installation of the backup or solar system. The installation must be compliant with SANS 10142 and ALL its parts. Any warranty claim submitted without installation photos, a valid Coc and proof of a qualified wireman/master electrician installing the unit, can be rejected and will render the warranty claim null at void.
The warranty does not cover damage resulting from:
- · Power surge
- · Under-voltage
- · Over-voltage
- · Lightning
- · Corrosion
- · Sea spray
- · Condensation
- · Water damage
- · Dust or any solid particles
- · Sand
- · Insects
- · Lizards
- · Excessive heat exposure
- · Weather damage
- · Negligence by the installer or homeowner
- · Incorrect installation
- · Inadequate protection device rating
- · Tampering (broken seal)
- · Dirty filters
- · Exceeding the maximum power rating, current or voltage for the input solar circuit, DC battery input, AC input and AC output.
The warranty will be void if the unit is:
- · Not installed as per manufacturers specifications
- · Not installed with a minimal 40kA surge protection unit for both live and neutral wires from the AC incoming supply
- · Not installed with a minimal 40kA surge protection unit for both positive and negative wires from the AC incoming supply
- · Not protected by the calculated and required 2 pole breakers for the input and output of the inverter
- · Not installed with a changeover switch
- · The battery input must be protected by a rated fuse for both the negative and positive connections, within the calculated PSCC ratings.
- · Tampered with (attempted to open the unit)
- · Visible damage to the unit